To install your charging station, the French law imposes since 2017 to appeal to a IRVE certified professional electrician (Recharge Infrastructures for Electric Vehicles). Carplug already works with a network of certified electricians, accessible here . More and more electricians are certified, and the simplest is often buying the terminal of your choice on our site , then ask the licensed electrician of your choice to install it near you.
It is important to check the total power of your electrical installation, and to deduce the maximum power consumption during peak consumption. You will then get the available power that will power your terminal. This step is important because the terminal will surely be the element that will consume the most in your home: a terminal of 11kW is equivalent to 11 small electric heaters. If the power is insufficient, it will be necessary to ask your energy supplier an increase of this one.
Example of calculation of available power:
A charging station must be installed on a dedicated line, with its own breaker coupled with its own differential switch . A release with current release is additional security not required, but allows you to obtain ZE Ready certification. Below are the specifications of these elements to be in good standing:
To make it easier for you to choose electrical protections, Carplug already offers packs compatible terminals and protections .
Below is an illustration of connection in both situations, in the case of a terminal HAGER Witty 2-22kW (source HAGER).
Section of connecting cables, according to French standards NF C15-100 and NF C15-722:
More information is available here:
Your specialist for your terminal projects
Need help? Contact our technical support
For advice on your projects
We are available from Monday to Friday from 9:00 to 18:00