Three-phase dynamic load management module - for three-phase HAGER charging station - XEV305 , also named XEV304 remote information simulator to dynamically manage the load your HAGER charging station-phase depending on the available power in your installation.
The kit contains management module 1 + 3 induction coils kits connect to the module
varies the charging current of the charging station based on the maximum available
avoids triggering the main circuit breaker
The management module is installed on the main power of the table
The coil moves around the stage that starts from the main breaker
Example of Use
For example, if you have at home a 40A single-phase installation, and that you have connected your HAGER Witty charging station 32A single phase on a dedicated line, then there is a good chance that your main circuit breaker trips during a load because your charging station will consume more than the available power.
The load management module will allow you to avoid this problem. It connects to the power of your table, and will measure in real time the total consumption of your home. The only adjustment to indicate is that the amperage of your main table, for example 40A here. The module will then be the difference between 40A and the consumed current, and will continuously supply the charging station with the maximum current available, without cutting out the installation.
So if your home consumes for example 17A, then your charging station will be supplied with 23A (40-17). When your house will consume less, 5A for example, then the charging station will be supplied with 32A (40-5, but limited to 32A maximum load current of the charging station).